Water purification systems in hemodialysis
- Nicholas Hoenich, PhD
Nicholas Hoenich, PhD
- Associate Member
- Institute of Cellular Medicine, Newcastle University
- Richard A Ward, PhD
Richard A Ward, PhD
- Professor of Medicine
- University of Louisville
The different water purification systems used in hemodialysis are reviewed here. Discussions concerning the waterborne contaminants to which hemodialysis patients are exposed and the methods of monitoring water purification systems used in hemodialysis are presented separately. (See "Contaminants in water used for hemodialysis" and "Maintaining water quality for hemodialysis".)
RATIONALE FOR WATER PURIFICATION SYSTEMS
All dialysis facilities require a properly designed and maintained water treatment system to safeguard patients . No municipal water can be considered safe for use in hemodialysis applications in the absence of a treatment system since some of the most toxic contaminants arise from municipal water treatment practices.
Hemodialysis patients are particularly vulnerable to contaminants in the water used to prepare concentrate and dialysis fluid or in water used for reprocessing dialyzers (see "Reuse of dialyzers", section on 'Reprocessing techniques'). This vulnerability is due to the following:
●Since water is the major constituent of dialysis fluid, compared with individuals who are not on hemodialysis, hemodialysis patients are exposed to extremely large volumes of water. The estimated water intake of a healthy individual is 2 L per day or 14 L per week. By comparison, during a single dialysis treatment lasting four hours, performed at a dialysis fluid flow rate of 800 mL/min, a hemodialysis patient is exposed to 192 L of water, or to 576 L per week, if treated three times weekly.
●Hemodialysis patients have inadequate barriers to such contaminants. In healthy individuals who are not on dialysis, the gastrointestinal tract separates blood from contaminants in the water. By comparison, the barrier between blood and water in hemodialysis patients is the membrane within the hemodialyzer through which transfer of contaminants is limited only by the molecular or particulate size of the contaminant.To continue reading this article, you must log in with your personal, hospital, or group practice subscription. For more information on subscription options, click below on the option that best describes you:
- Martin K, Laydet E, Canaud B. Design and technical adjustment of a water treatment system: 15 years of experience. Adv Ren Replace Ther 2003; 10:122.
- International Organization for Standardization. Water Treatment Equipment for Hemodialysis and Related Therapies, ISO 26722:2014, International Organization for Standardization, Geneva 2014. http://www.iso.org/iso/catalogue_detail.htm?csnumber=61864 (Accessed on June 28, 2016).
- Association for the Advancement of Medical Instrumentation, Water Treatment Equipment for Hemodialysis and Related Therapies, ANSI/AAMI/ISO 26722:2014, Association for the Advancement of Medical Instrumentation, Arlington, VA 2014. http://my.aami.org/store/detail.aspx?id=26722 (Accessed on June 28, 2016).
- International Organization for Standardization. Water for Hemodialysis and Related Therapies, ISO 13959:2014, International Organization for Standardization, Geneva 2014. http://www.iso.org/iso/home/store/catalogue_tc/catalogue_detail.htm?csnumber=61862 (Accessed on June 28, 2016).
- Association for the Advancement of Medical Instrumentation, Water for Hemodialysis and Related Therapies, ANSI/AAMI/ 13959:2014, Association for the Advancement of Medical Instrumentation, Arlington, VA, 2014. http://my.aami.org/store/detail.aspx?id=13959 (Accessed on June 28, 2016).
- European best practice guidelines for haemodialysis (Part 1). Nephrol Dial Transplant 2002; 17(Suppl 7):50.
- Kawanishi H, Masakane I, Tomo T. The new standard of fluids for hemodialysis in Japan. Blood Purif 2009; 27 Suppl 1:5.
- Tokars JI, Miller ER, Alter MJ, Arduino MJ. National surveillance of dialysis associated diseases in the United States, 1995. ASAIO J 1998; 44:98.
- Do VT, Tang CY, Reinhard M, Leckie JO. Effects of chlorine exposure conditions on physiochemical properties and performance of a polyamide membrane--mechanisms and implications. Environ Sci Technol 2012; 46:13184.
- Arnow PM, Bland LA, Garcia-Houchins S, et al. An outbreak of fatal fluoride intoxication in a long-term hemodialysis unit. Ann Intern Med 1994; 121:339.
- Pérez-García R, Rodríguez-Benítez P. Chloramine, a sneaky contaminant of dialysate. Nephrol Dial Transplant 1999; 14:2579.
- Calderaro RV, Heller L. [Outbreak of hemolytic reactions associated with chlorine and chloramine residuals in hemodialysis water]. Rev Saude Publica 2001; 35:481.
- Junglee NA, Rahman SU, Wild M, et al. When pure is not so pure: chloramine-related hemolytic anemia in home hemodialysis patients. Hemodial Int 2010; 14:327.
- Meyer MA, Klein E. Granular activated carbon usage in chloramine removal from dialysis water. Artif Organs 1983; 7:484.
- Farmer RW, Kovacic SL. Catalytic activated carbon offers breakthrough for dialysis water treatment. Dial Transplant 1997; 26:771.
- Dunsmore BC, Jacobsen A, Hall-Stoodley L, et al. The influence of fluid shear on the structure and material properties of sulphate-reducing bacterial biofilms. J Ind Microbiol Biotechnol 2002; 29:347.
- Soini SM, Koskinen KT, Vilenius MJ, Puhakka JA. Effects of fluid-flow velocity and water quality on planktonic and sessile microbial growth in water hydraulic system. Water Res 2002; 36:3812.
- Libman V. Use of Reynolds number as a criteria for design of high-purity water systems. Ultrapure water 2006; 23:26.
- Bek MJ, Laule S, Reichert-Jünger C, et al. Methemoglobinemia in critically ill patients during extended hemodialysis and simultaneous disinfection of the hospital water supply. Crit Care 2009; 13:R162.
- Davidovits M, Barak A, Cleper R, et al. Methaemoglobinaemia and haemolysis associated with hydrogen peroxide in a paediatric haemodialysis centre: a warning note. Nephrol Dial Transplant 2003; 18:2354.
- International Organization for Standardization. Guidance for the preparation and quality management of fluids for hemodialysis and related therapies, ISO 23500:2014, International Organization for Standardization, Geneva, 2014. http://www.iso.org/iso/catalogue_detail.htm?csnumber=61863 (Accessed on July 04, 2016).
- Agar JW, Perkins A, Heaf JG. Home hemodialysis: infrastructure, water, and machines in the home. Hemodial Int 2015; 19 Suppl 1:S93.
- Mackler BA, Merkle JC. Current knowledge on groundwater microbial pathogens and their control. Hydrogeol J 2000; 8:29.
- RATIONALE FOR WATER PURIFICATION SYSTEMS
- OBTAINING A WATER TREATMENT SYSTEM
- WATER PURIFICATION PROCESSES
- Reverse osmosis
- Carbon filtration
- Other purification processes
- - Softeners
- - Filters
- - Chemical injection
- WATER STORAGE AND DISTRIBUTION
- ASSEMBLING A WATER TREATMENT SYSTEM
- INSTALLING A WATER TREATMENT SYSTEM AND VERIFYING ITS PERFORMANCE
- WATER TREATMENT FOR HOSPITAL BEDSIDE DIALYSIS MACHINES
- WATER PURIFICATION SYSTEMS FOR HOME HEMODIALYSIS
- SUMMARY AND RECOMMENDATIONS